NOTE: The Ceiling Mount system must be installed by a qualified HVAC-R technician. Failure to have the system installed by a
qualified technician will void the warranty.
|Cellar Size||1000 cu. ft.*||2000 cu. ft.*|
|BTUh w/85° air entering the
|Dimensions||Evaporator: 12.75”H x 14.5”W x 35.75”D • Condenser: 13.5”H x 12”W x 18”D|
|Voltage Rating||115V or 230V (subject to availability)|
|Weight||Evaporator: 80 lbs • Condenser: 56 lbs||Evaporator: 80 lbs • Condenser: 69 lbs|
|Amps (starting/running)||Evaporator: 2/1 • Condenser: 23.5/6.8||Evaporator: 2/1 • Condenser: 43.6/8.7|
|Drainline||1/4” ID clear plastic tubing|
|Installation||Evaporator unit is installed through the cellar ceiling; the condenser is installed up to 100 ft away|
|Thermostat||Digital display with 50-ft. cable and 50-ft. liquid-temperature-measuring bottle probe|
|Temp. Delta||55°F temperature differential between the cellar temperature and condenser air intake temperature|
|Warranty||Two-year limited warranty (parts and labor)|
*Each wine cellar is unique and has specific cooling requirements . Heat load calculations should always be performed prior to selecting a cooling unit.